Since we are all expected to stay at home during this time of social distance we would appreciate your consideration for the foregoing request.
RFP #M20210810 -Air Purification
Q&A for RFP Air Purifiers
1) I received notification of this bid opportunity for air purification devices; however, I was unable to find the type of units that would be needed for Rutherford County Schools.
Do you have other bid documents available that would specify the type of units being requested or the square footage the items to cover? Any other information you can provide about the air Purification units being requested would be greatly appreciated.
I have provided the square footage below for all schools. The area needed in our maintenance, transportation, and technology department is less than 35,000 square feet and might require a visit to these locations to determine the exact square footage. You are welcome to visit any and all locations prior to the submission deadline. Please let me know if you would like to do this, and I will notify our schools.
As for the type of units. We are open to most types, however, we do not want HEPA filters that would require frequent changing nor any unit that produces ozone as specified in the RFP.
Square Footage - RCS
Chase High - 104,185
Chase Middle - 101,619
Cliffside - 52,844
Cool Springs - 47,200
FC-Dunbar - 59,000
East High - 106,674
East Middle - 105,574
Ellenboro - 93,786
ROC - 53,199
Forrest Hunt - 62,352
Pinnacle - 69,225
Harris - 72,084
Mt. Vernon-Ruth - 62,500
RS Central - 244,741
RS Middle - 129,335
Rutherfordton - 83,983
Spindale - 61,785
Sunshine - 62,221
#M20210720--Carver Parking Lot
#T20210720 Structured Cabling for New Middle School
#T20210720 Structured Cabling for New Middle School Q & A
Typing errors in RFP:
Fiber patch cables need to be OS2 single mode not OM2 and fiber patch cables need to be "SC to LC" not ST to LC.
1. In building area E306 the Band/Chorus Classroom does not have a "WAP" triangle/symbol on the blueprint for the ceiling however there needs to be a quad in the ceiling.
2. Some CCTV locations were left off of the blueprint, please refer to the information located at question 15 below.
Q&A for RSMS RFP
Q1. Our team is asking for additional time to prepare our response. Can you confirm if you and the county can approve an extension to the deadline and possibly move the deadline to the beginning of the week of August?
A1. We can not extend the RFP deadline
Q2. Due to the fact that (vendor name redacted) is not an approved Avigilon vendor, would you be willing to accept a cabling only bid for the security scope of work?
A2. We are looking for a complete proposal covering all of the work described in the RFP and vendors have the option to subcontract parts of the work provided that it is all detailed and quoted within their proposal.
Q3: Is there a schedule as to when the work will need to be finished if awarded the project?
A3: Substantial construction completion of the school is scheduled for late January. Due to delays with the RFP, we will need work on this cabling project to begin as soon as possible and finish in a timeframe that does not hinder the construction completion timeline.
Q4: Will 3000v UPS’s suit the needs of each IDF?
Q5: Is there a preferred UPS manufacturer?
Q6: Is there a preferred manufacturer for classroom instruction audio?
A6: None is needed for this RFP, Not Applicable
Q7: Will an IP based system such as AES be approved for classroom audio, common area paging, and bell scheduling as a combined solution?
Q8: Is there a specified color for the panic strobe and can the annunciator and strobe be a single integrated unit?
A8: I asked and we do not use panic strobe lights at any locations.
Q9: Who does the panic button need to notify if pressed?
A9: Call 911
Q10: Is the contractor responsible for providing and installing the TV’s? If yes is there a preferred manufacturer and is a smart TV required?
A10: TV’s not applicable for this RFP, just the CAT6A cabling to the labeled areas. (Future)
Q11: RFP calls for 12 strand OS2 fiber between MDF and IDFs with 6 strands being terminated. Are the remaining 6 strands to be left dark/unterminated?
A11: Dark fiber. Labeled if code requires unterminated cabling to be labeled (I’m unsure).
Q12: RFP calls for OM2 ST to LC fiber patch cables. Is this correct, or do OS2 SC to LC patch cables need to be subsituted?
A12: This was a typing error, it is suppose to be “SC” to LC Patch cables.
Q13: RFP calls for classroom WAPs to have 4 Cat6a per location and other WAP locations to have 2 per. Is this correct?
A13: The ones labeled WAP’s one will be used for access points (installed by us) and the other ports for future use. So 4 in classrooms and smaller workrooms that have WAP’s listed they would be 2. This is of course in addition to the ones on the walls labeled. When it lists “WAPs” that means what will initially installed near this panel, etc. No wireless AP’s should be bid out, this will be handled in another RFP/etc.
Q14: RFP states that selection of rack types (4/2 post) or wall mounted vented cabinets was TBD. Is this still the case?
A14. Yes, 4 post in MDF, and wall mounted in IDF’s unless this is impossible/then 2 post. Needs to allow enough space for Ruckus ICX-7550's and other rack equipment which is over 16" deep.
Q15: We are seeing external mounted cameras, but no interior cameras on the drawings. Is this correct?
A15: We apologize for some of the areas not making it to the blueprint. There will need to be max 30 Avigilon CCTV cameras, all entrances and viewing down hallways, cafeteria, gym and office front desk area. At least 2-3 exterior cameras need to be analytical and we would like at least 1 be set to read tag plates at the front entrance.
Q16: RFQ states the installation of 12 strand OS2 fiber for the backbone cabling system between MDF/IDF locations. Patch cords are listed as OM2, is this meant to be OS2 patch cords?
A16: This was a typing error, is suppose to be OS2 patch cords.
Q17: Will fiber be expected to be installed within conduit pathway from the buildings MDF to each of the buildings IDF locations? Would armored fiber be an acceptable alternative to conduit?
A17: Yes, armored fiber will be acceptable.
Q18: Sheet E100 under Security the 1st Note says “all intrusion system devices shall be routed in surface raceway where exposed or on existing wall to above ceiling”. Is this raceway currently installed or is the contractor expected to provide & install it?
A18: According to the project manager the general contractor (Beam) will install.
General Contractor will provide:
- Door contacts for simple security
- Pathways for door access
- Cable trays at the main corridor
Q19: RFP states that GC has provided some cableways and j hooks. Does this mean Notes S1 and S3 on sheet E402 have been installed?
A19: Yes, will be installed. Some of J hooks may be installed by GC after speaking with awarded vendor, coming on site, etc. All j hooks provided.
Q20: Will the electrical be installing the fire sleeves or will we be responsible for them?
A20: The selected RFP vendor will be responsible for fire sleeves as the GC didn't know what size would be needed. RFP vendor will also provide approved caulk/fire stop for the fire sleeves as well.
Q21: We have seen both 11:00 and 3:30 for due times tomorrow on the quotes. Which one is it?
A21: It is 3:30PM. It is incorrect in one location on the RFP PDF. Sorry for the error!